1. The installation site should be well ventilated, the generator end should have sufficient air inlet, and the diesel engine end should have a good air outlet. The area of the air outlet should be more than 1.5 times the area of the water tank.
2. The area around the installation site should be kept clean to avoid placing nearby items that can produce corrosive gases and vapors such as acid and alkali. Conditional fire extinguishing devices should be provided.
3. If it is used indoors, the exhaust pipe must be opened to the outside, the diameter of the pipe must be more than the diameter of the pipe of the muffler, and the elbow of the pipe to be connected should not exceed 3 to ensure the smooth discharge of smoke, and should be The pipe is inclined downwards by 5-10 degrees to avoid rainwater injection; if the exhaust pipe is installed vertically upwards, a rain cover must be installed.
4. When the foundation is made of concrete, the level should be measured with a level Gauge during installation to fix the unit on a level basis. There should be a special shock pad or foot bolt between the unit and the foundation.
5. The unit casing must have a reliable protective grounding. For generators that need to be grounded directly at the neutral point, the neutral point must be grounded by a professional and equipped with lightning protection devices. It is strictly forbidden to use the grounding device of the mains to carry out neutrality. Point directly to ground.
6. The bidirectional switch between the generator and the mains must be very reliable to prevent reverse power transmission. The wiring reliability of the bidirectional switch is subject to inspection and approval by the local power supply department.
7. The wiring of the starting battery must be firm.
AOT ELECTRONIC TECHNOLOGY CO.,LTD which has 15 years experience in diesel generator spare parts manufacturing. We provide full kinds of generator spare parts for engine replacement and other related electric products such as automatic transfer switch, electric Relay etc. Welcome to contact us for more information.
Contact: Ms.Lika (Sales)
Phone: 0086 182 5072 9722
Add: Unit 1405, 2000 Xiangfu Road, Xiamen City, China